# RV Electricity – The ABCs of campground power and grounding – Part 1

AC power and grounding from the electric pole to your RV

I recently realized after trying to explain to an electrician the facts of how electricity gets from the electric pole into your RV outlets, that there were no basic diagrams to be found. So I’ve started making drawings of the entire layout, which I’ll publish here. While this looks complicated at first glance, it’s really pretty straightforward. Part 1 today will cover how it’s all hooked up according to the National Electrical Code, which also shows how the neutral and ground wires are bonded (connected) together in the power company incoming service panel, but nowhere else. And Part 2 next month will cover all the various load and fault current paths, including how to integrate a generator with a floating neutral into your RV’s electrical system.

Where to begin?
Most of you have never seen a schematic diagram of what’s on the electric pole coming into the campground or your own house, so here’s where the power begins for you.

Starting at the left side of the diagram (click any image to enlarge) you’ll see there’s a transformer either on the pole or on a pad being fed with around 7,000 volts of electricity. Yes, those are what we call primary wires since they carry electricity from the substation to the campground’s power transformer. The reason why the voltage is up as high as 7,000 volts is to reduce the voltage drop over the miles of wire connecting you to the power company. And indeed it starts out much higher than that on the big high-tension lines you see going across the fields, with 110,000-, 250,000- and 500,000-volt feeders being pretty common. Again, higher voltage equates into less current for a given amount of wattage, and less current equals less voltage drop. Take my word for it now, but someday I’ll show you all how Ohm’s Law works.

Transformers
The purpose of the power company transformer is to step-down the incoming 7,000 volts to 240-volts. And as you can see, that 240-volt winding is also split down the middle to create a pair of 120-volt outputs. You’ll also find that the bottom of every electric pole in the USA has a ground rod/pad installed, which functions as a place for lightning strikes to find “ground.” OK so far?

This power company transformer then feeds 240/120-volt power to the campground’s incoming service panel. You have the same thing in your own house, which might be a 100- or 200-amp service. For future discussion you should know that a 100-amp service can supply 100 amperes of current at 240 volts, or 200 amperes of current at 120 volts. And a 200-amp service can supply 400 amperes of current at 120 volts. Many campgrounds have a 400-amp (or larger) service panel because they need to feed power to multiple pedestals.

Neutral-ground bonding
You should also see that the service panel includes a Neutral-Ground bonding point, which is typically a green screw in the neutral bus bar which bonds (connects) it to the metal box and service panel grounding rod that’s installed at the campground. This is how modern electrical code works, but it’s possible to find really old installations that do some strange grounding things. More on that MUCH later.

Now let’s take a look at what’s inside of a campground pedestal. You’ll see that it has incoming Hot 1, Hot 2, Neutral and Ground wires. The two Hot Legs (as they’re often called) go to several circuit breakers powering the various outlets in the pedestal panel. So there’s a double-pole 50-amp breaker feeding the 50-amp/240-volt outlet (50 amps x 2 = 100 amps at 120-volts), a single-pole 30-amp breaker feeding the 30-amp outlet, and a single 20-amp breaker feeding the 20-amp outlet. Yes, the 20-amp outlet must be GFCI protected according to code, but for simplification I’m going to ignore that on this diagram.

What, no ground rods or neutral bonds?

One thing that you’ll see missing on the campground pedestal is a separate ground rod or neutral-ground bonding screw. There will be a ground wire bonding screw from the green/ground bus to the metal box, but that’s NOT connected to the incoming neutral wire. Again, the G-N (Ground to Neutral) bonding point is only done in the incoming service panel, and NOT the sub-panel or campground pedestal. This ground wire is technically called an EGC or Equipment Grounding Conductor, and is only allowed to carry FAULT current (when something goes wrong), and not LOAD current (which is what you draw to power your RV appliances). Again, this G-N bonding point (as well as an earth grounding rod) is only included on the incoming service panel, NOT the campground pedestal, which is wired just like a secondary circuit breaker panel in your house.

The RV connection
Finally, the power is fed from the outlet in the pedestal into the power distribution center of your RV, where it has its own incoming 20-, 30- or 50-amp circuit breaker, and outgoing 15- and 20-amp breakers to feed your air conditioner, 12-volt converter, microwave, etc. I’ve simplified this diagram without the output breakers to show that there’s definitely NO Neutral-Ground bonding screw in this box, but there IS an EGC (Equipment Grounding Conductor) connected to an RV chassis bonding point. This connection is what eliminates any hot-skin/stray-voltage on your RV chassis (and skin) in the event of a fault current caused by normal internal appliance leakage, or even something like a metal screw poked through a wire accidentally. (Hey, stuff happens.)

Time to power down…
Wow, I think that’s enough for now. As you can see, there’s a very specific order as to how all of this hooks up, and there can only be ONE Ground-Neutral bonding point at the campground’s incoming service panel. And there are no ground rods at your RV or the pedestal. So what’s all this mysterious naming of Grounds, Ground-planes, Earth Grounds, Ground Rods, Equipment Grounding Conductors, and Neutral-Ground Bonds? Yes, they’re all different things and have different functions. But if you’re going to wire ANYTHING connected to 120 volts, then you need to know the difference. So stay tuned to the next RVelectricity issue #13 and learn how it all works. See you then.

In the meantime, let’s play safe out there (especially around electricity)…

Mike Sokol is an electrical and professional sound expert with 40 years in the industry. Visit NoShockZone.org for more electrical safety tips. His excellent book RV Electrical Safety is available at Amazon.com. For more info on Mike’s qualifications as an electrical expert, click here.

##RVT869

## 12 Thoughts to “RV Electricity – The ABCs of campground power and grounding – Part 1”

1. Suka's Mom

Great article; however, your drawings need a spell-check. I think you want credit to “RVelectricity 2018.”

1. Mike Sokol

Well, I never said I could spell, so thanks for the heads up. Of course I not only got the spelling wrong on the first graphic, I simply copied and pasted it into the next two graphics.

2. Steve Barnes, Kamloops, BC

A subject of general interest for publication and to include at Quartzite would be how to install an inverter in a RV that only has a converter. 15 years ago larger 5 ths came with both; no longer so.
.
At Quartzite would I have to attend all 3 days to see all your seminars? Do you have the schedule yet.

1. Chuck and I don’t have a plan for which seminars I’ll be doing on any particular day, which is one of the reasons I did a survey. We should know more in a few weeks and will do an announcement then.

3. John

I got to *attempt* to explain to a park owner (it’s a mobile home park with one site converted to an RV site) that the 30 amp plug is not 240 V, it’s 120. The owner had been a licensed electrician in a previous life, and was sure he was looking at an old 240 volt dryer plug. Fortunately, apparently the first person who attempted to plug in, tested voltage (or had a good surge protector in his setup) and discovered the problem and fixed it before any rigs got destroyed.

In my case he replaced the 30 amp plug with a 50 amp plug and circuit breaker, properly. The pedestal, being installed for a mobile home originally, had a 200 amp service.

1. As I’ve noted elsewhere, I get at least several emails like this every month, and sometimes a few every week. Even though the TT-30 receptacle is plainly marked to 125 volts maximum, many old-school residential electricians simply can’t believe it’s “only” 120 volts. That’s one of the reasons I think that EVERY RV owner with a 30-amp connection needs an Intelligent/EMS surge protector. It only takes a few seconds of 240-volts on a TT-30 outlet to destroy most of the electronics in your RV. An intelligent surge protector that can disconnect you from incorrect voltage is way cheaper.

4. Tim

Well done!

1. Thanks… I carry this around in my head, so it’s about time I put it all down on paper.

5. Al Simons

Hi, Mike.
This is a timely article. I was just in a campground that had a ground wire/rod on the pedestal. Is this simply unnecessary, or harmful? The pedestal was mounted on a “telephone” pole. If harmful, how is this different from the style of pedestal that is metal all the way down to the ground? If it makes any difference, this campground is on a flood plain, and floods frequently. (I don’t think it makes a difference, but I’m not the expert!)

On a separate note, a possible other rally topic would be an SVP gathering if/when you could get enough attendees to make it worthwhile. Perhaps Quartzsite? Looking forward to meeting you there.
-Al

1. An extra ground rod and wire at a pedestal isn’t a problem, and it’s not a code violation. However, it’s not a substitute for a proper low-impedance (less than 1 ohm) ground wire connection to the EGC neutral/ground bonding point back in the incoming electrical service panel.

6. Yeah, I get a least a few emails a month about electricians and home owners who install a 30-amp/120-volt outlet for their RV. The TT-30 (Travel Trailer-30 receptacle) does indeed resemble an early 30-amp/240-volt dryer outlet found in many homes, So wiring one with 240-volts will do a lot of expensive damage in seconds if you plug your RV into one.

7. mike

Well done. A request I get a lot as an electrician is to install a 240 rv outlet. First question I ask is 30 am or 50 amp. Most of the time it’s 30, so I have to explain it’s a 120 volt, not a 240 volt. A lot of people see the big plug and automatically think it’s 240, or they think the big prongs are 2 hots and the 3rd is a ground, not realizing it’s 1 hot, 1 ground, and 1 neutral. I even had 1 guy trying to rig up 2 extension cords to feed an rv outlet. He figured plugging 1 end in the top of the outlet would give 120 and the other end in the bottom would give him another 120. That was a tough chore explaining it doesn’t work that way.

This site uses Akismet to reduce spam. Learn how your comment data is processed.